### Power system architectures for the commercial buildings – Part Two

In the previous Topic; Power system architectures for the commercial buildings – Part One , I explained the first type of Power system architectures for the commercial buildings which was “Low building, type 1: One supply section” and today I will explain the second type; Low building, type 2: Two supply sections as follows.

You can also review previous topics about electrical design requirements for commercial buildings for good following-up:

2- Low building, type 2: Two supply sections

Conditions for using this power system architecture:

1- If the following rule is verified:

The number of building floors must not exceed the max. Number of floors for Two supply sections (i) calculated by equation#1.

If:

Max. Side length of the building = a (in meter)

One Floor area A = a2 (in square meter)

Height per floor = h (in meter)

Then:

Max. Number of floors for Two supply sections (i) ≤ (100 – 2a) / h    (equation#1)

If the number of floors exceed the max. Number of floors for one supply section (i) calculated by equation#1, then we must use other types of power system architecture.

Note: all buildings have number of floors ≤ 4 are low rise buildings.

2- If the floor area of the building > 2,000 m2.

Note: if floor area > 2,000 m2, so there will be more than one (≥ 2) central equipment room per floor feed from the LVMD (Low Voltage Main Distribution switchgear).

3- If the power density of the building loads have the following limits:

• Power required >2,000 kW.
• Segmentation of power required 85 % utilized area (i.e. functional area like Offices, Briefing rooms, Data center, Canteen kitchen with casino, Heating/ventilation/air conditioning, Fire protection and Transport) And 15 % side area (i.e. shafts, fountains, green area, sky lighting area and etc.).

4- If the power supply needed for the building have the following requirements:

• Supply types 100 % total power from the public grid; (Supply of all installations and consumer Devices available in the building).
• 10–30 % of the total power for safety power supply (SPS) from generators; (Supply of life-protecting facilities in case of danger, e.g.: Safety lighting, Elevators for firefighters, Fire-extinguishing equipment).
• 5–20 % of the total power for uninterruptible power supply (UPS); (Supply of sensitive consumer devices which must be operated without interruption in the event of a NPS failure / fault, e.g.: Tunnel lighting, airfield lighting, and Servers / computers and Communications equipment).

Example
for " Low building, type 2: Two supply sections " power system architecture:

We have a building with 2,400 KVA total load power, 4 floors and floor area 2,500 m2 with total area 10,000 m2.

Solution selected for this building is using the Two supply section power system architecture as follows:

 Design solution Advantages of this solution Benefits from this solution Using Two supply sections per floor Supply at the load center, short LV cables, low losses Low costs, time savings during installation Radial network Transparent structure Easy operation and fault localization Transformer module with 2 × 1200 kVA, Minimization of voltage fluctuations, lower statics requirements on building structures Optimized voltage quality, Cost minimization in the building construction work Redundant supply unit: – Generator 730 kVA (30 %) (the smaller the generator, the greater the short-circuit current must be compared to the nominal current) – UPS 400 kVA (15 %) Supply of important consumers on all floors in the event of a fault, e.g. during power failure of the public grid Increased reliability of supply Safety power supply Safety power supply in acc. With DIN VDE 0100-718 Supply of sensitive and important consumers Uninterruptible supply of consumers, e.g. during power failure of the public grid Use Medium-voltage switchgear from type SF6 gas-insulated Compact switchgear; independent of climate Minimized space requirements for electric utilities room; no maintenance required Use Transformer from type cast-resin with reduced losses Low fire load, indoor installation Economical Use Low-voltage main distribution with  central grounding point ( which splitting of PEN in PE and N to the TN-S system) EMC-friendly power system Protection from electromagnetic interference (e.g. to prevent lower transmission rates at communication lines) Use Wiring / main route as cables Central measurement of current, voltage, power, e.g. for billing, cost center allocation Cost transparency Use Connection inside substation ( Transformer – LVMD- NPS – SPS) as busbars Easy installation

For this example the power system architecture will be as follows:

 " Low building, type 2: Two supply sections " power system architecture

Where:

 NPS Normal power supply PCO Power company or system operator FF Firefighters HVAC Heating – Ventilation – Air conditioning MS Medium-voltage switchboard LVMD Low-voltage main distribution SPS Safety power supply UPS Uninterruptible power supply z Power monitoring system

In the next Topic, I will explain the “High-rise building, type 1: Central power supply, cables” power system architecture. So, please keep following.