Power Factor Correction Capacitors Sizing Calculations – Part Eight

Today, we will continue explaining Power Factor Correction Capacitors Sizing Calculations Steps in detail as in the previous article “we only listed the Power Factor Correction Capacitors Sizing Calculations Steps.

So, today we will continue explaining other steps for Power Factor Correction Capacitors Sizing Calculations For Existing Installations:

 4- Power Factor Correction Capacitors Sizing Calculations Steps

 Now, we are going to explain the Power Factor Correction Capacitors Sizing Calculations Steps for Different Cases of Installations: For Existing Installations, For New Designs.

 4.1 Power Factor Correction Capacitors Sizing Calculations Steps For Existing Installations

 the Power Factor Correction Capacitors Sizing Calculations Steps For Existing Installations include two phases as follows: Preliminary Evaluation Phase, Design Phase. Fig.1 shows the phases of Power Factor Correction Capacitors Sizing Calculations For Existing Installations. Fig.1

 First: Preliminary Evaluation Phase

 The preliminary evaluation is performed to determine if the application of power factor correction capacitors is likely to be economical or not. Fig.2 shows a typical flow chart for the preliminary evaluation process. Fig.2

 Step#4: Make Preliminary Measurements For Harmonics

 This step is used to help identify and report potential harmonic problems. 20% of industrial plants cannot operate capacitors without some careful attention to the harmonics. This means that 80% of industrial plants will not have problems, but it is wise to study any possibility for harmonic effects in the initial evaluation. Measuring Harmonics The measuring instrument used to make the preliminary measurements in step#2 should have the capability to report harmonics as well. The key things to determine by measurements with respect to harmonic distortion are: Main bus voltage distortion; Measure the THD including all harmonics and, also, individual harmonic magnitudes in percent, of fundamental. Harmonic content of load currents, particularly those in suspected harmonic-producing loads such as adjustable-speed motor drives. The THD and rms values are needed as well as magnitudes of individual harmonics. Representative harmonic current in existing capacitor banks, at least the THD and rms values. Analysis of Harmonics Measurements Based on the above harmonics measurements, a harmonics study will be required if any of the following conditions are found: Harmonic-producing devices (such as adjustable-speed drives and arc furnaces) are a large portion of the load, The main bus voltage distortion is greater than 2%, The distortion of the total plant current is greater than 10%. Important Notes: As you take the power intervals, take periodic harmonic samples. If the load varies considerably, such as rolling mills, veneer lathes, etc., take several measurements to try to capture the worst case. If practical, measure the distortion of currents in existing capacitor banks. Existing capacitors are the best locations to find harmonic currents that might indicate that there is a harmonics problem. Unfortunately, capacitor leads are not always easily accessible. However, it is strongly recommended that you open one or two cabinets and measure the current. If you do not have a meter capable of showing the individual harmonic, measure the rms current with a suitable true rms ammeter. If the rms current measured is much higher than the expected rated current, there is likely to be a harmonics problem. Lack of high current in capacitors does not indicate that there will be no problems after the addition of capacitors. it only indicates that there are no harmonics now. The instruments for monitoring harmonics range from permanently installed 3-phase monitors to hand-held single-phase devices. Most of the modern ones are capable of transmitting data to a computer for further analysis. While there are numerous instruments available for measuring harmonics, proper harmonic measurements and the proper interpretation of the results will generally require someone with special training in this field.

 Step#5: Repeat the Economic Screening Worksheet

 This step is used to include the cost of studies and harmonic mitigation- if it is required - in the cost of the capacitor costs worksheet. In step#3, we ignore including costs of the harmonic study. Then, if there are significant harmonic sources or existing distortion, come back to the capacitor costs worksheet, add in the estimated study cost in step j & cell L23, and re-compute the economics in the Economic Evaluation Worksheet. Harmonic studies range from \$3000 to \$7000 for smaller industrial plants. Studies for large plants might typically be \$15000 and up.

 Step#6: Compare the Savings with the Probable Cost of Capacitors' Installation

 This step is to determine if the capacitors' installation process - after adding the harmonic study costs - still economical or not? And we will have two cases as follows: Case#1: If the capacitors installation is still economical with these considerations, you may proceed with reasonable confidence that an economical and effective capacitors installation can be achieved and you can proceed with the design phase. Case#2: If the capacitors installation is no longer economical with the harmonic considerations, you have two options: Option#1: Stop the process if you feel certain that harmonic mitigation will be needed and not economically justifiable.Option#2: Proceed uneconomically into the design phase with the hope that the harmonic problems will not severely impact the installation, which happens frequently, and with the understanding that it may not be possible to find a capacitor scheme that is economical according to your criteria.

 Example#1 Using the same data for example#1 in article " with taking into consideration the harmonics study cost of 10,000 USD. Solution The solution by using our Economic Screening Worksheet is shown in below images: Results The worksheets indicate that a relatively simple fixed capacitor installation that costs approximately \$30 per kvar is uneconomical based on a three year evaluation period and interest rate 7%. So, we can stop the process or proceed uneconomically to the design phase.  The simple payback period is predicted to be about 3.12 years.

 Second: Design Phase

 In this phase, we will design and select the best economical, efficient and applicable power factor capacitor scheme for an installation. Fig.3 shows a typical flow chart for the Design process. Fig.3

 Step#1: Performing a Detailed Plant Survey

 This step is used to collect sufficient data about the plant to determine the optimal size of capacitor to place in each location. It includes the following sub-steps: Step#1.A: Review the one line diagram. Step#1.B: Take into consideration the loads that produce harmonics. Step#1.C: collect sufficient data Inventory by using measuring instruments.

 Step#1.A: Review the one line diagram Review the one line diagram of the facility to determine the most appropriate form of power factor correction. The one-line diagram must show the main structure of the electrical system from the utility interconnection up to at least the main motor control centers and larger sub panels. You must note the Major types of loads, step-down transformers, and approximate locations for existing capacitor banks. Figure-4 shows an example of a simple one-line diagram. The main buses are indicated by the heavy bars and are labeled with the rated bus voltage. All significant transformers and loads (particularly nonlinear loads) should be indicated. Complete the one-line diagram as you proceed with the detailed load inventory. Supply the diagram to contractors and engineers you may choose to assist with the application. This will enhance communications considerably. Fig.4: Simple One-Line Diagram

 A Simplified method to collect sufficient data Inventory by using measuring instruments After you do the initial economic screening, you should have a good idea of what you can afford to spend on studies, inventories, and the like. When the budget for power factor correction does not justify a detailed inventory and analysis, the following are suggestions for less extensive load measurements: Monitor only the main feeds. Measure, at least, snapshots of the rms currents in the main cables to get an idea of how the load inside the plant divides. Assume the overall plant load shape for all loads. In lieu of demand interval data, several snapshots at different times will suffice. Obviously, the more data collected, the more likely it is that the capacitors will be added to portions of the plant where they will do the most good. The greatest benefits will be achieved on lines that have high current with respect to ampacity, poor power factor, and long cable runs. Therefore, make special note of loads and cables with these characteristics.

In the next article, we will continue explaining other steps for Power Factor Correction Capacitors Sizing Calculations for Existing Installations. Please, keep following.

The previous and related articles are listed in below table:
 Subject Of Previous Article Article Glossary of Power Factor Correction Capacitors Types of Loads, The Power Triangle, What is a power factor? Types of power factor Why utilities charge a power factor penalty? Billing Structure. What causes low power factor? Bad impacts of low power factor, Benefits of Power Factor correction. How to make Power Factor Correction? Types of Power Factor Correction Capacitors Individual compensation Group compensation, Central compensation, Hybrid compensation. Summary for Power Factor Correction Capacitors Sizing Calculations Steps Step#1: Collect Monthly Billing Data Step#2: Make Some Preliminary Measurements For Current And Voltage Step#3: Fill the Economic Screening Worksheet

 Back To